## NEC Table 250.66: Grounding Electrode Conductor for Alternating-Current Systems

NEC Table 250.66: Grounding Electrode Conductor for Alternating-Current Systems

NEC Table 250.66: Grounding Electrode Conductor for Alternating-Current Systems

Table 310.15(C)(1) Adjustment Factors for More Than Three Current-Carrying Conductors

Table 9 in the National Electrical Code is provides copper and aluminum conductor resistance and reactance data. Units of resistance and reactance are ohms per… Read More »NEC Table 9 Alternating-Current Resistance and Reactance for 600-Volt Cables, 3-Phase, 60 Hz, 75°C (167°F) — Three Single Conductors in Conduit

Use the Bruns Engineering AC voltage drop calculator vdrop.brunsengineering.com to quickly and accurately calculate voltage drop.

Table 310.16 is one of the most commonly used tables in the National Electrical Code. The reason is the inherent practicality and breadth of installations… Read More »NEC Table 310.16 Ampacities of Insulated Conductors with Not More Than Three Current-Carrying Conductors in Raceway, Cable, or Earth (Directly Buried)

The Smart Panel Schedule engine automates the tedious process of creating, editing and maintaining panel schedules. No more spreadsheets or hand written, barely legible schedules.

NEC Table 250.122: Minimum Size Equipment Grounding Conductors for Grounding Raceway and Equipment

How to calculate hydraulic power in crude oil piping systems.

Overview The alternating current (AC) induction machine is ubiquitous in modern life, by far the most widely used of all electric machines. The success of… Read More »Alternating Current Induction Generators

Estimate Voltage Drop This table was calculated using the equation $latex V=I(R cos(\phi) + X sin(\phi))$ where $latex V$ is voltage, $latex I$ is current,… Read More »AC Voltage Drop Calculation Table